Important Note : Never Test
Pumpset In Dry condition. Pure Water Must completely Be Filled In Motor &
Casing Of Pump Before Testing, Testing Period Must Not Exceed 15 Seconds. Even
For Testing of Motor Only, Water Must Be Filled In It Before Testing. During
Testing Period, Water Must Continuously Be Poured On Oil Seal Of Motor. To Check
Alignment Of Complete Pumpset, Move Shaft Assembly By A Screw Driver
Upward-Downward. The Shaft Assembly Will Lift 1 to 2mm When Alignment Is Proper. All
Precautionary Measures As Specified In Given Manual, Must Be Adhered Carefully.
T66 Series – Submersible
Pumpsets Are Suitable Fore Borewell of Minimum 6" (150mm) or Bigger Size.
Maximum Outer Diameter of Pumpsets is 142mm. The Pumpsets Comprise Motor of 6"
(150mm) & Pump of 6" (150mm).
All Above Models Are 3-Phase,
350/440 Volts, 2820/2880 RPM, 50 Hz & 2 Poles. (All Models Up To 3HP Can
Also Be Made Available in 1-Phase, 200/260 Volts, 2820/2880 RPM, 50 Hz & 2
7.5 HP Submersible Pumpsets
With SD = ) (Delta Connection) (Double Cable) Can Also Be Made Available.